Please can I use the charm ''DI 24 Vdc Dry Contact" instead of ''DI Namur'' ?
The charm is to connect a Namur limit switch valve.
I think I have a big problem here
Thanks in advance for your help.
This is the official online community site of the Emerson Global Users Exchange, a forum for the free exchange of non-proprietary information among the global user community of all Emerson Automation Solution's products and services. Our goal is to improve the efficiency and use of automation systems and solutions employed at members’ facilities by sharing our knowledge, experiences, and application information.
User Groups |
World Areas |
Community Guidelines |
Legal Information |
Contact Community Manager
Website translation provided by
© 2015-2022 Emerson Global Users Exchange. All rights reserved.